Home » Shop » 2006 – Specialist Dam Safety Instrumentation for Identifying and Monitoring Earthquake Damage at Aviemore Dam, New Zealand
P Amos, N Logan, and J Walker
There are a number of geological faults in close proximity to Aviemore Power Station in the South Island of New Zealand, including a fault in the foundation of the 48m high earth dam component of the power station. Possible movement of the Waitangi Fault in the earth dam foundation is of particular concern for dam safety, and the effects on the dam of a fault rupture has been the subject of detailed investigation by the dam’s owner Meridian Energy Ltd. These investigations have concluded that the dam will withstand the anticipated fault displacement related to the Safety Evaluation Earthquake without catastrophic release of the reservoir.
The identification of damage to the dam following an earthquake and monitoring of the dam to identify the development of potential failure mechanisms are important for determining the post-earthquake safety of the power station. The first stage of the post-earthquake response plan is the quick identification of any foundation fault rupture and damage to the dam to enable immediate post-earthquake mitigation measures to be initiated, such as reservoir drawdown. Following initial response, the next stage of the post-earthquake monitoring programme for the embankment dam is longer term monitoring to identify a changing seepage condition due to damage to the dam that might lead to a piping incident. Such an incident may not occur immediately after an earthquake, and it can be some time before the piping process becomes evident.
This paper presents some key instrumentation installed at Aviemore Dam and included in the emergency response plan for the post-earthquake monitoring of the embankment dam.
ANCOLD is an incorporated voluntary association of organisations and individual professionals with an interest in dams in Australia.